On this page we have brought together the most important questions and answers on the LUXORliving Smart Home system.
A maximum of 64 individual LUXORliving devices are intended.
Yes, this is possible at any time. The system can be configured in detail – apart from scenarios, which have to be set later on via the clients (tablets/mobile phones).
Once programming is complete, I can then go into the building, import the hardware and use drag & drop to assign the devices to the program – done!
No, you can integrate any button from the market into the system. With the TA2 I T4 I T8 integration modules, all floating contacts can be integrated; with the REG module B6, non-floating buttons or motion detectors can also be incorporated.
Yes, the dimmers are based on the highly successful KNX series hardware and are specially designed for professional LED use. The various settings also allow certain adaptations to be made to the lamp.
Yes, the switching modules are based on the highly successful KNX series hardware and are specially designed for professional LED use. Inrush currents of up to 800 A/200 microseconds are no problem.
No, unfortunately this is not possible.
Windows, iOS and Android.
Yes, this is possible with the LUXORplay version for Windows.
No, you don't need one. There is also the option to connect a laptop directly to the IP1.
Once the bus voltage has been applied, the IP1 needs to wait at least 30 seconds to 1 minute, then it should be ready for operation. If you still cannot connect, check the following:
In general, all basic functions remain available. Only control with the app (clients), scenario requests and their saved options, as well as the time and presence functions are then out of action until further notice.
Yes, this is generally possible. All controls related to lighting and shading remain available. Only control with the app (clients), scenario requests and their saved options, as well as the time and presence functions are then out of action until further notice.
Yes, as the administrator you are able to grant access rights or, if necessary, to revoke them at any time.
The D2 and D4 dimmers were specifically designed for dimming LEDs and deliver excellent results.
Besides controlling radiators and underfloor heating, a cooling function in the building can also be supported.
With a little technical understanding, you can carry out virtually any adjustments in the functions. However, it is better to have an electrician carry out adjustments in the installation/wiring work.
The LUXORliving system can be expanded at any time. However, note that you must not exceed a maximum of 64 system components.
You need an Internet connection, a WiFi network and a connection between the LUXORliving IP1 system control centre and the WLAN router.
Yes, if you have set up a VPN connection via the WLAN router you can access your building from anywhere. If you have installed a camera, you can even see what is going on at home.
You can integrate up to 10 IP cameras into your app at any time.
The LUXORliving system uses a communication language that has been tried and tested for many years and has been implemented successfully a million times over.
The hardware is based on KNX devices which have been successfully used in the field for decades. These devices are equipped with very robust relays that can withstand inrush currents of up to 800 A without damage in the case of LED control.
No, the LUXORliving system and apps are free. If, for example, you would like to integrate an Alexa voice control system, the provider's annual fee must be taken into account.
Ask your local electrician. The system is very easy to install and start up, and, if required, our trained experts can also help you via our hotline.
In order to detect the current room temperature, you’ve to use a T 4/ T8 or an actuator S1 e.g. to affiliate a temperature probe floor sensor (9070321), temperature sensor IP 65 (9070459) at input C3 and C4. The finally desired temperature has to be set via the app.
This option is feasible, if a VPN access is set on the mobile phone. No matter, if an IP address or DHCP setting has been chosen (please find some example settings in a separate document)
No, in case of a faulty appliance, the hardware has to be replaced by a device.
Afterwards you will have to start the search function from the menu to reconnect with the system. This may take up to 2 minutes. The newly detected device will be listed in green coulour, the faulty one is displayed in red.
Now drag the green entry upon the red entry and drop it. Then start downloading the programm again. Don’t forget to prepare LUXORplay as well.
IP1 Master RESET (Note: The password for IP 1 is set back to default (admin). Project data will be erased afterwards)
Select RESET in the display, confirm the selection by pressing RETURN. Now choose MASTER RESET from the available options and hold the RETURN button for approx.10 secs.
If the RESTART DEVICE function is selected, only the LUXORliving IP1 is restarted. No data is lost, but all active connections to the system are interrupted for a short time.
Device RESET for all LUXORliving devices (Attention - after that, the device has to be configured from the very beginning)
In general, 2 actuators (24V AC) can be directly connected to each heating actuator of the LUXORliving series.
However, if more is needed in larger rooms, a grouping of channels is necessary.
If, for example, the light is to be controlled in a toilet and a fan is operated in parallel with just one triggering button, then this function can be used.